Repair on the tap separation from the house sewer line PVC.
Sewer cleanout under the back deck stair case. Sewer is PVC inside the foundation out to the cleanout. PVC sewer line out from the cleanout to the city sewer. City sewer is 47′ out from the clean out approximately 8′ in depth. PVC sewer line has a separation between the house sewer line and the tap connection. Ground water is infiltrating the separation and roots are in the break. Recommend sewer line repair at this time. Sewer is draining at this time. Sewer from the house to the fitting at the tap house side are in good working condition. Tap fitting connection to the house sewer separated.